Climatic, Environmental and Fire Behaviour (C2 E2 F1) Test of Cast Resin Transformer
American Journal of Electrical Power and Energy Systems
Volume 7, Issue 1, January 2018, Pages: 11-15
Received: Feb. 19, 2018;
Accepted: Mar. 5, 2018;
Published: Apr. 2, 2018
Views 1744 Downloads 207
Remya Krishnan, Design Department, Federal Transformers Co. LLC., Abu Dhabi, UAE
Muraleedharan Nair, Federal Transformers Co. LLC., Abu Dhabi, UAE
Follow on us
The dry type cast resin transformer shall be suitable for usage under expected climate conditions. It shall be self-extinguishing and shall not produce toxic gases in the event of fire. This is verified by the Climatic, Environmental and Fire withstand behaviour test as per 60076-11. This paper gives the design features of a 1600 kVA dry type cast resin transformer which was subjected to climatic, environmental and fire behaviour (C2 E2 F1) tests at KEMA testing laboratory, Netherlands. The technical parameters of epoxy resin system, winding configuration, and clamping, etc. necessary to meet the requirements are also discussed.
Cast Resin Transformer, C2 E2 F1 Test, Dry Type Transformers, Special Test for Power Transformers
To cite this article
Climatic, Environmental and Fire Behaviour (C2 E2 F1) Test of Cast Resin Transformer, American Journal of Electrical Power and Energy Systems.
Vol. 7, No. 1,
2018, pp. 11-15.
Copyright © 2018 Authors retain the copyright of this article.
This article is an open access article distributed under the Creative Commons Attribution License (http://creativecommons.org/licenses/by/4.0/
) which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
IEC 60076–11 - (2004) - dry type transformers.
IEC 60332–3–10 - Test for vertical flame spread of vertically mounted bunched wires or cables.
Hunstman datasheet for Araldite casting system.
C57.12.91-2011 - IEEE Standard Test Code for Dry-Type Distribution and Power Transformers.
C57.12.01-2015 – IEEE Standard for General Requirements for Dry-Type Distribution and Power Transformers.
IEC 60076-1; 2011 Power Transformers part 1 General.
IEC 60076-3 – Power Transformers Part 3 Insulation levels, dielectric test and external clearances.
Federal Transformers – technical brochure “Cast Resin Transformers”
IEC 60085 – Electrical insulation - Thermal evaluation and designation.
IEC 60270 – High Temperature techniques – Partial Discharge Measurements.